I have a copy of the NEC, but I know that I NEVER find the answer there.
RCM, on the other hand, is sure to have it.
Can I run a 240v receptacle and a 120v one off the same breaker? Sized
appropriately, of course. Say a 2-pole 20A breaker, 3-wire 12ga cable,
and 20A receptacles, like this:
N ........... 240v receptacle
|__________ 120v receptacle
It looks OK to me, but one never knows what esoteric considerations the
NEC might make.
- posted 8 years ago