The website can be found at http://mc-group.ca

I would really appreciate any feedback regarding these calculators.

I would really appreciate any feedback regarding these calculators.

I would really appreciate any feedback regarding these calculators.

How are you calculating voltage drop? Your calculator does not give the same voltage drop as the K method.

Example the following is pretty much standard for electricians in the USA: VD = 2 x K x L x I /CMA (multiply by .866 for three phase three wire and by .5 for three phase four wire) K = 12.9 ohms per circular mil foot for copper and 21.2 for aluminum (required by State of Washington) L = equals one way circuit length in feet I = current in amperes CMA = circular mil area of conductor from Chapt 9 Table 8 of the NEC

### Contant Voltage level

- - next thread in ⏚ Electrical Engineering

### Custom-made Fiber Bragg Grating

- - previous thread in ⏚ Electrical Engineering

### need help with an electromagetic field project

- - newest thread in ⏚ Electrical Engineering

### where's all the political slagging-match gone?!

- - the site's newest thread. Posted in ⏣ General Metalworking