Hi everyone. I have 15 amp rated light switches on a 20 amp circuit. These
light switches in most cases control overhead lights (in a kitchen, garage,
dining room). Is this alright, or do I need to use 20 amp rated light
switches?
Also, on a 20 amp circuit, I have 15 amp rated electrical outlets? Is this
alright? Some of these outlets are controlled by a 15 amp light switch as
well, is that alright? Thanks for any help.

Happens every day in residential. .
There is a section in the NEC to allow this in residential.
Usually the switch controls less than the circuit ampsity so there is little
danger.

"Eric and Megan Swope" wrote in
message news:vuxce.646$KP.630@trndny02...
circuit. These
kitchen, garage,
rated light
outlets? Is this
light switch as
The breaker is there to protect the *wiring so it doesnt over
heat and catch fire. for a 20 amp breaker in the US you must
have size 12 awg wire... that can feed multiple circuits, each
of which can carry less current of course,
If your wire is size 14 you must use 15 amp *breaker
Theoretically you could plug something into one of your 15 amp
recepticles that drew 20 amps. and would tend to be hard on
the 15 amp recepticle...but your wire would still be protected
since its 12 gage and you have a 20 amp breaker,
You are not supposed to run more than 15 amps full load on a
20 amp circuit continuous, the 20 amps is a peak,
intermittent rating...but thats not controllable...so they NEC
does the best it can with regulations in a real world.
There is significant safety margin built into the rules so
that 21 amps is not going to burn your house down instantly,
Maybe 25 or 30 amps would be a significant problem though...
20 amp recepticles will last longer in use near the 15 amp
range than lighter ones...but in most cases thats not a big
usue.. loads over 12 amps or so on a 110 receptical are
rear..my skill saw only draws 12 at full load.
.
Phil Scott

Actually 80% = 16A. (Continuous is over 3 hours; 20A for the first 3
hours is OK. Fuses and thermal trip circuit breakers can trip at a 20A
load over 3 hours.)
Also could use "Spec Grade" receptacles.
Bud--

OOPS Typo! Yes, try this again. the load is required to be the same
or less than the switches rating.
That's why I say check the NEC. No typo's in there!
:)

PolyTech Forum website is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.