13 years ago
I am running to a sub panel in a detached garage from my main panel
for about 210 feet. I have talked to many people locall and get
I finally called the inspector and got a different answer than he had
told me previosuly. Once he told me #4 copper with a # 6 ground and
another time he told me #3 copper with a #6 ground.
He said I cant use the 2-2-4-6 wire the local supply house is tryign
to sell me. He said aluminum would have to be #1 if in conduit and 1/0
if direct buriable. He said copper would be cheaper.
I dont want to tick the guy off but what should I do at this point?