I have a 251 ft^3 Argon/CO2 mix tank, and little (60ft^3 ?) tank of the
same. Once the little one runs out, I was wondering it would be
possible/safe/not-stupid to transfer from the big tank to the little one
by hooking them together and opening the valves. If one were to do
such a thing, would I do it with a regulator on it, or with none?
Is this a good idea?
It is called Cross-filling, and it used to be quite common, but due to
insurance reasons most shops and suppliers are forbidden from doing it.
I have a cross-fill hose for neutral gasses and one for oxygen.
The hose is a very special stainless steel braid, teflon hose, good to
about 6000 psi.
These are the same hoses used on tank manifolds.
You connect each end of the hose to a tank.
Open the empty tank's valve, all the way.
Then open the full tank's valve all the way.
The sound is quite ...surreal, as the gas rushes into the empty tank.
It takes about 1 or 2 minutes for the pressures to equalize.
As a demonstration of basic physics, you will find that that the source
tank gets colder and the recieving tank gets warmer.
Once the pressures have equalized, close both valves and very slowly
undo one of the hose fittings.
You will get a blast of high pressure gas from the hose when you break
the connection, but that is just what was in the hose.
Western Enterprises sells the hoses.
Any welding supplier can order one for you.
"Ernie Leimkuhler" wrote: (clip) The hose is a very special stainless
steel braid, teflon hose, good to about 6000 psi. (clip)
I do this all the time with oxygen. Instead of a hose, I have two
regulator/tank fittings hooked together with a high pressure elbow. The
welding supply counter man who helped me set this up suggested just barely
cracking one of the valves, so the fill takes place slowly. This minimizes
the heating in the tank being filled.
If you close off and disconnect while the tank is still hot, you get less
fill.This really only matters after the supply tank starts to get low, since
that means I am not getting a good fill on my small tank
Ernie, why does it matter which valve you open first?
The concept that semi-trained people were handling tank refills got the
insurance companies worried.
All the Seattle welding suppliers stopped doing it several years ago.
All the tanks go back to the plant for refill.
Any time a tank is refilled it is supposed to be checked for hydro date and
a visual inspection. Most people either don't know to do this or just don't
do it out of laziness, therefore worried insurance companies.
It would be nice to have a pressure gage teed into the charging hose.
This would be must have item if your were charging from 350 cubic foot
with 3000 psi to 40 cubic foot cylinder rated at 2250 psi. The best
time to cascade charge is from full cylinder to empty cylinder. The
small cylinder might be used for protable welding or reserved for when
large cylinder runs out.
As described, you would put a small amount of contamination (from the
air in the hose) in the tank being filled. I would leave the fitting a
little loose on the tank being filled and gently crack the valve on the
source tank briefly.
"Ted Edwards" wrote: (clip) I would leave the fitting a little loose on
the tank being filled and gently crack the valve on the source tank briefly.
Another reason for doing this: If the hose has been lying around, and
anything combustible has got inside, sudden application oxygen at tank
pressure could cause an exposion. (Say a spider is living inside, for
example.) I was taught by a welding-shop supervisor to attach theO2
regulator to the tank, but not to fully tighten it. Then crack the tank
valve, and finish tightening the fitting to stop the leakage. If anything
starts to go wrong, your hand is already on the wrench, so you can loosen it
quickly. The same procedure would apply to the transfer hose. In fact, I
would suggest blowing a little O2 through it by cracking the supply valve
briefly, before attaching the empty tank.